UL-Listed Notification Appliance Circuit (NAC) synchronization using System Sensor, Wheelock, or Gentex “Commander2” appliances.
Operates as a “sync-follower” or as a “sync-generator” (default). See note on page 2.
Contains two fully-isolated input/control circuits – triggered from FACP NAC (NAC expander mode) or jumped permanently “ON” (stand-alone mode).
Compatible with coded inputs; signals passed through.
In stand-alone mode, output power circuits may be configured as: resettable, (reset line from FACP required), non-resettable, or a mix of two and two.
AC trouble report selectable for immediate 2-hour delay.
Requires input trigger voltage of 9 – 32 VDC.
Includes integral battery charger capable of charging up to 18 AH batteries. Cabinet capable of housing 7.0 AH batteries.
Tìm hiểu thêm: